The Sensorbox 2 is out of stock. New stock is expected before the end of the year.
The SmartESVE Sensorbox v2 has three inputs for CT's (current transformers), a voltage input to determine the direction of current flow, and a P1 port for reading a smart meter (DSMR 5, mainly used in the Netherlands). The connection to the SmartEVSE is via a 4-pin plug.
The difference with the Senosrbox v1 is that it is now possible to determine the direction of the current, and thus to charge the car on pure solar power. The Sensorbox v2 only works in combination with software version 2.10 or higher of the SmartEVSE.
The sensor box can be connected to a smart meter with the P1 connection. Use the supplied RJ12 cable. The smart meter must support the DSMR 5 protocol.
Tested smart meters:
- Iskra AM550-TD2 (OK)
- Landis+Gyr e360 (OK)
- Sagemcom T210-D (OK)
- Kaifa MA304H4CNL (OK)
It is always possible to use the current transformers if the smart meter is not compatible or available.
These must be purchased separately, and are of the type SCT-013-000 or SCT-010TL.
Furthermore, the Sensorbox has a status LED, which blinks orange when power is taken from the grid, or green when it feed back to the grid.
The program port can be used to reprogram the module with a micro-USB cable (not included).
Placement of the sensor box
To be able to measure the total current of all devices, the sensor box must be placed near the mains distribution panel.
If a suitable smart meter is installed, it can be connected using the RJ12 cable.
Otherwise the current transformers (CT's) should be used.
If CT's are used, the voltage input (220-240V) must also be connected.
Clip the CT's around the loose phase wires, try to find out which wire is L1, and connect it to connection 1 of the sensor box.
From the same phase a voltage connection must be made to the MAINS input of the sensorbox.
Then connect the CT's of phase L2, and L3 (if available).
Make a 4 wire connection with the SmartEVSE, using the 4 pin green plug.
Cat5 cable can also be used for this wire. The length of the cable can be up to 100m.
The delivery consists of:
Sensor box v2
RJ12 to RJ12 data cable, length 1M
Power supply cable IEC-320-C7, length 2M
This evaluation kit is intended for use for ENGINEERING DEVELOPMENT, DEMONSTRATION, OR EVALUATION PURPOSES ONLY and is not considered by Stegen Electronics to be a finished end-product fit for general consumer use. Persons handling the product(s) must have electronics training and observe good engineering practice standards. As such, the goods being provided are not intended to be complete in terms of required design-, marketing-, and/or manufacturing-related protective considerations, including product safety and environmental measures typically found in end products that incorporate such semiconductor components or circuit boards. This evaluation kit does not fall within the scope of the European Union directives regarding electromagnetic compatibility, restricted substances (RoHS), recycling (WEEE), FCC, CE or UL, and therefore may not meet the technical requirements of these directives or other related directives.